WLC-4000-Fill W/High Alarm
NEVER REPLACE An Electronic Level Controller or Float Again!
WLC-4000 - Fill w/ High Alarm - Electronic Water Level Control | Complete Kit Includes Sensor With 50 ft. Sensor Wire, Controller, and Mounting Assembly | Fill w/ High Alarm | TWO-CONTACT POINT SYSTEM | Custom Sensors lengths available upon request | 6-wire Dry contacts to BAS for measuring Fill “ON” time, High Water Alarm and fault conditions. () Operates any 110VAC valve & 110VAC audible alarm (Not supplied in this kit.)
FILL WITH HIGH LEVEL SET POINT – WITH INTERNAL DIAGNOSTIC TEST SYSTEM
WaterLine Controls™ WLC-4000 Specification – Set Points for: Fill With High Alarm
The Model WLC-4000-110-50 (This is a sensor wire length of 50 Feet) Waterline Controls Unit manufactured by System Dynamics, Inc (888-905-1892) and supplied by System Dynamics, Inc (888-905-1892) shall be supplied as a unit, including sensor with wire, controller and mounting assembly parts. A properly sized slow closing solenoid valve shall be supplied by others. The level control system shall consist of solid-state parts with non-corrosive components and is suitable for use outdoors in an industrial application or indoors in a mechanical room environment. The level control system will provide automation monitoring outputs, fine control, ease of operation, ease of service and accessibility. The Control Panel shall come with a Limited Lifetime Warranty, which can be copied from: http://waterlinecontrols.com/pdfs/Lifetime_Limited_Warranty%5B1%5D.pdf and submitted.
The cooling tower water level control system shall be automatically controlled within a 1-1/2” range identified as “the operating range” (this range can be changed by a custom ordered probe). The level control system shall also monitor for a high water level condition. These conditions have three outputs each which are: 1. Close a set of dry contacts for the BAS, 2 - operate a relay rated at 30AMPS for 250VAC and 3 - turn on an LED to indicate this sensor has tripped. The Fill dry contacts can be used as a comparative to develop a baseline benchmark of water usage for the system
The water level control system shall be comprised of a sensor mounted inside a 3” sensor housing with wire attached that is suitable to be placed in a wet environment and installed at the water level. A separate control panel, which is to be mounted outside of the wet environment within a distance of less than 50 feet (1,000 feet is the maximum length of a sensor wire that can be supplied). A solenoid valve supplied by others and installed in-line to provide make-up water.
The 3” sensor housing shall be installed according to the drawings. The sensor head shall be mounted inside the catch basin area at the water level in a safe and convenient location according to the drawings using the “U” bolts and mounting bracket provided. The sensor head and its assembly will consist of 3 inch PVC pipe, four pre-cut ¼” round stainless steel probes. The adjustment of the sensing system shall be accomplished by moving the 3” PVC mounting sleeve up or down in its mounting bracket and “U” bolt. The 3” sleeve will have three holes: two holes near the top of the pipe to allow air to move through the pipe and a third hole centered in the middle of the operating range to be used as the water level reference point for an accurate water level.
The Control Panel must be certified by an independent third party testing facility (e.g., UL or ETL) to meet Standard UL508 or equivalent for the country in which it is installed. The level control panel shall draw no more than 0.25AMPS at 110VAC or 0.125 Amps at 220VAC. All power relays shall be rated at 30Amps at 250VAC for the normally open relays and 20Amps at 250VAC for all the normally closed relays. All four level outputs shall have a corresponding set of normally open dry contacts rated at 0.5Amps at 60Volts to be connected to an automation system.
The Control Panel shall have visual displays indicating power to the level control panel, when the control panel is actively filling and the high water alarm. The control panel shall have a self-test button which cycles through and turns on each function in sequence for at least 10 seconds to allow for trouble-shooting as needed. This trouble-shooting feature shall operate without removing wires or disconnecting the sensing probes. This feature will be automatic and activated by pushing a button. There shall be an indicator (a Yellow LED) to indicate that this feature is operating. The Control Panel shall have an indicator which tells the operator when there is debris fouling the probes. The Control Panel shall have an automatic reset system if the fill valve stays on for longer than six hours without turning off. It shall have a corresponding set of dry contacts that alerts (Closing a dry contact) the automation system.
The Control Panel shall be of modular construction such that relays that control the above features can be removed and replaced without replacing the PCB or transformer.
The Solenoid valve shall be brass and sized according to the drawings and shall be normally closed, 110VAC at 0.9Amps at a peak and supplied by others.